Views: 0 Author: Site Editor Publish Time: 2022-02-25 Origin: Site
In useWindshore roomIn the process, sometimes the phenomenon of the wind shower is not blowing, the following points are several cases often encountered by daily customers, and can be referred to the failure.
(1) First check whether the power switch and the emergency stop switch are in turn on, if two reasons are not, check the circuit, and the leakage switch is closed.
(2) Whether the FUSE fuse configured by the IC board is blown, such as the fuse of the fuse, the 4A fuse is required.
(3) Check if the micro switch and the photoelectric switch move, if there is no action, the micro switch and photoelectric switch should be replaced.
(4) If the AC contactor does not work, it affects the blow, and the AC contactor is required.
(5) If the circuit board cannot output a signal in an AC contactor coil, it is necessary to change the IC circuit board.
(6)Windshore roomIt is not allowed to open the door when it is blown, and if you encounter an emergency, you can stop the shutdown on the emergency stop.
After more than ten years of industry experience sedimentation, Xinli Environment has always adhered to the service tenet of \"customer interests above all \", and continuously develop new products through technology improvement and upgrading, our strength and product quality have been recognized by the industry. From R & D to after-sales, all products have multiple quality tests, strict control, layer, and do not worry.
All high-efficiency air filters are completed in the purification workshop, and will be tested by scanning, ensuring the performance indicators of the high-efficiency filter, and can produce high-efficiency filters required for various non-standard specifications in accordance with user requirements. Service hotline: 4006883551 / 13165316200!
Disclaimer: The above content is from the network, copyright belongs to the original author, such as copyright issues related to works, please let us know to process in time!