The wind speed is high, the resistance is high. If the service life of the filter is based on the final resistance and the wind speed is high, the service life of the filter is short. It is difficult for general users to actually observe the influence of wind speed on filtration efficiency, but it is much easier to observe the influence of wind speed on resistance.
Now, takeair filterTechnology, so that the concentration of dust particles in the clean room or local purification area is controlled within the allowable range to ensure the level of cleanliness requirements. Shandong snyli Purification Technology Co., Ltd., with more than ten years of experience i
According to the \"Code for Clean Room Construction and Acceptance\", its efficientair filterThe following methods are available for leak detection:1. Scanning by leak detector methodThe air filter to be detected for leaks must have been tested for air volume, which is between 80% and 120% of the de
air filterIt is the core equipment of the air-conditioning purification system of the clean room. The filter forms resistance to the air. As the dust accumulation on the filter increases, the filter resistance will increase. When the filter has too much dust and the resistance is too high
1. Initial effectair filterIt is suitable for primary filtration of air-conditioning system, mainly used to filter dust particles above 5μm. The primary air filter has three styles: plate type, folding type and bag type. The outer frame materials include paper frame, aluminum frame, and galvanized i